Wind Solar Hybrid Street Light
Solar Street Lighting
Wind Solar Hybrid Off-grid Sys
Controller & Inverter
HY-H12GOS 12KW Wind Solar Hybrid Off-grid System
● Wind Power: 6000W rated power output - 2pcs HY-3000 Wind turbine, 110V
● Solar Power: 6075W rated power output - 45pcs 135W 12V polycrystalline solar panel
● Controller & Inverter: off-grid wind solar hybrid controller inverter 5000W
● Standing free 11 meter tower for 2pcs 3000W wind turbine
● Rooftop solar panel installation bracket for 6000W PV
Estimated System Yearly Power Production(KWH) - solar and wind combined
Remarks: solar power production is estimated based on areas with class II solar resources (yearly sunshine 3000-3200hrs, radiation level 6570-7621MJ/㎡), wind power production is estimated based on annual average wind speed at 10 meter high free-standing tower installation, you may input your project site latitude & longitude at following website, so you can get more accurate figure of your local wind and solar resources.
● Simple cottage with 300-400 bedrooms, providing very basic power for total load less than 5000W.
● Ideal solution for areas with stable public grid supply to reduce your electricity bill.
● Ideal solution for areas with unstable public grid supply as a reliable power backup system.
● Areas completely without public grid supply, HY-H12GOS system could serve as a stand-alone power supply system, such as remote area or holiday cottage.
System Installation Requirement
● Rooftop solar panel installation requires minimum 48 square meters, south-facing steep roof is recommended for better solar power harvesting
● Open space without tall obstacle is preferred for wind turbine installation for better wind power harvesting.
● A 4-5 square meter storage room is preferred to place controller inverter system and batter bank
|Wind turbine||HY-3000 x 2 110V, 5 blade|
|PV modules||135W (14V) x 45|
|Wind Solar Hybrid off-grid controller Inverter||input: 6000W wind/6000W solar|
|Output: 5000W 110-240Vac 50/60hz|
|Grid by-pass switch: optional|
|Deep Cycle battery AGM gel||200AH x 18|
|PV module mounting bracket||flat roof/tile roof/corrugated Metallic roof/ground mount|
|Suggested Tower installation||HY-FRK30 (4m) for flat roof installation|
|HY-HT30-10.4P3 hydraulic tower 10.4 meters|
|HY-HT30-13.4P3 hydraulic tower 13.4 meters|
Recommended household electric appliance-HY-H12GOS-Super
1. System inverter is designed with total capacity 5000W, which means total load capacity of the house should be no more than 5000W, inverter will automatically shut down if instant load over 5000W for system self-protection, so we suggest end user estimate your own house total load capacity, and then select the proper inverter system.
2. Above household daily power consumption is calculated based on a typical usage of an ordinary household for end user reference only.
3. Air conditioner is not recommended for this system because air conditioner is a high power consumption unit which consumes 5-8KWH, if the house has to be equipped with air conditioner, we suggest supply the power for air conditioner from public grid.
4. There is an optional by-pass switch which could automatically switch to public grid power when there is not enough power in battery bank, this is only applicable to the area with public grid connection.